Step 1: Bury Conduit and Build a Platform of solar Mounting System
Bury conduit from the house or building that will receive the power to the area where the solar panel array will be located.
With the conduit in place, build a platform consisting of concrete pillars and 4x4s that will support the solar array.
Step 2: Mount the Panels with solar mounting system
Once the platform is finished, the experts are ready to get started. For the solar array, the team uses eight 24-volt 110-watt PV panels that have been pre-fastened to create the array. For the upstairs loft, four 12-volt, 255-amp sealed batteries will store power collected by the panels. And finally, a 5500-watt power inverter and 40-amp charge controller will be installed in the garage near the standard electrical box. This expandable system should produce 35,000 watt hours per month -- enough to power a deep well water pump, interior lights and a few appliances of solar mounting system.
Moving on, the team mounts the panels to the platform. Angle brackets are used at the mounting points, and the front feet are mounted first. The feet are squared and centered before being secured into place.
Step 3: Secure the Rear Legs
Use meteorological data to determine the proper angle for the array, then elevate and secure the rear legs.
Step 4: Wire the Solar Modules
Wire the solar modules together and join them at a junction connector or fuse combiner box. The modules should be stripped and wired in pairs before being connected to the fuse box mounted at the platform and connected to underground conduit output cables.
Note: When performing any electrical work, remember to take all safety precautions. Because of the danger involved, intricate electrical work is often best left to professionals solar mounting system.
In the terminal box, the stripped wires must be connected properly. In this instance, the red wires are connected to the positive terminal, and the black wires to the negative terminal. Once connected, the wires are fed up through the bottom of the junction box and connected to the corresponding positive and negative terminal blocks.
Step 5: Understand the Wire Connections
With the solar array assembled, correctly angled and wired, it's time to connect the exterior wiring to the interior control panels. The solar breaker will first be connected to a circuit breaker disconnect. The energy will flow from the disconnect to a charge controller and then to a battery bank to be stored. When needed, energy flows from the batteries back to the circuit breaker disconnect and from the disconnect to a power inverter (this will change the power from DC to AC). Finally, this converted power will flow into an electric panel -- where it will provide electrical power for the home solar mounting system.
In this instance, a back-up gas generator and well pump are also connected to the solar system. To handle all this, the solar installer recommends the installation of two 240-volt power converters to the right of the main breakers. All of the components -- including the new converters -- must be connected to the home's main electrical system to function solar mounting system
Step 6: Connect the Cables to the Control Panels
Run the electrical cable from the solar array into the house through the underground conduit. Connect the cables to nylon rope for easy threading, then pull through the conduit to inverter panels solar mounting system.
Connect the cables at the fuse combiner box located at the base of the solar array. The green cables are first connected to the grounding strip. The red cables are connected to the PV out positive terminal block; and the black cables are connected to the PV out negative terminal block.
Step 7: Ground the System
To finish the exterior work, tap a grounding rod into the earth near the array. Leave the long rod extending above the ground about 6"
Run copper grounding wire from the rod to the fuse box and from the solar panels to the fuse box.
Step 8: Make the Electrical Connections Inside
After the grounding wire is run, make the proper electrical connections inside. Run the cables from the array to the inverter panel disconnect. Again the red wire is connected to the positive terminal; the green grounding wire is connected to the grounding terminal; and the black wire is connected to the negative terminal.
The team installs the battery bank in the loft area above the new control panels. First, run conduit through the ceiling into the inverter panel. Next, feed two heavy-duty battery cables into the panel disconnect. The other ends of the cables will be connected to the battery pack.
The battery system must be installed in a series -- alternating positive and negatives -- and secured into place.
Complete final tests and attach the component covers.